2017-10-24 07:36 AM - edited 2017-10-24 09:07 AM
Needing to relocate FAS2240-4 and have to provide input power requirements. Power will be 110V. Anyone know the required Amps? Documentation talks about amps in relation to heat dissipation - just want to make sure I am figuring the totals correctly.
Solved! SEE THE SOLUTION
2017-10-24 08:00 PM - edited 2017-10-24 08:03 PM
FAS2240-4 with 24 x 4TB SATA drives at 110V would be 5.5A Typical, 6A worst case, and output 1,855BTU typical, 2,022 BTU worst case